SUPA GUTTER PUMPER’S anti-vortex baffle prevents air spiralling down the vertical drop once the water depth exceeds 25 mm, allowing the pipe to flow full of water. Gravity then pulls this full flow downwards, creating a vacuum that sucks water into the pipe at high velocity. **Longer vertical drops generate higher flow rates.**

**The first vertical drop must prime the second vertical drop to generate higher flow rates.** To ensure the second drop primes, the total of the length of the initial horizontal pipe *plus an equivalent 0.6 metre pipe length for each 90° elbow and an equivalent 0.3 metre pipe length for each 45° elbow *between the Gutter Pumper and the second vertical drop is recommended to be **not more than fifty times the length of the first drop**. The first drop’s length is measured from the top of the initial horizontal pipe to the gutter PLUS 25 mm from the gutter to the top of the anti vortex baffle.

**EXAMPLES:**

A 100mm drop will prime a**3.8 metre** initial horizontal pipe **plus** 2 x 20mm 90° elbows (**1.2 metres**).

A 300mm drop will prime a**13.2 metre** initial horizontal pipe **plus** 3 x 20mm 90° elbows (**1.8 metres**).

Pipework must remain vertical or horizontal.

A 100mm drop will prime a

A 300mm drop will prime a

Pipework must remain vertical or horizontal.

Clean gutter of all debris prior to installation. Gutter Pumper presents a minimal obstruction but gutters must be kept clean. If leaves are a problem, AQUATREK recommends the Fielders Watergate zinc gutter mesh. Watergate is suitable for most 115-125 mm wide eaves gutters and is sold in 8 x 1.25 metre packs.

**The first vertical drop must prime the second elbow and vertical drop to generate higher flow rates.** To ensure the second drop primes, the total of the length of the initial horizontal pipe *plus an equivalent 0.6 metre pipe length for each 90° elbow and an equivalent 0.3 metre pipe length for each 45° elbow *between the Gutter Pumper and the second vertical drop is recommended to be **not more than fifty times the length of the first drop**. The first drop’s length is measured from the top of the initial horizontal pipe to the gutter PLUS 25 mm from the gutter to the top of the anti vortex baffle.**EXAMPLES:**

A 100mm drop will prime a **3.8 metre** initial horizontal pipe **plus** 2 x 20mm 90° elbows (**1.2 metres**).

A 300mm drop will prime a **13.2 metre** initial horizontal pipe **plus** 3 x 20mm 90° elbows (**1.8 metres**).

DO NOT slope pipework. Pipework must remain vertical or horizontal.

DO NOT increase the 20 mm pipe’s diameter as this will break the vacuum but increasing the ground level HORIZONTAL pipe’s diameter reduces friction loss and is recommended for long runs.

Clean gutter of all debris prior to installation. Gutter Pumper presents a minimal obstruction but gutters must be kept clean. If leaves are a problem, AQUATREK recommends the Fielders Watergate zinc gutter mesh. Watergate is suitable for most 115-125 mm wide eaves gutters and is sold in 8 x 1.25 metre packs.

| |

Use a 32mm hole saw to drill a hole in a flat area on the bottom of the gutter near the gutter's high point. Eaves gutters are installed with a W pattern to allow slope and downpipes are plumbed at the low point. | |

Place the Gutter Pumper into the hole with a washer on either side and the gutter and face the baffle’s lowest edge towards the gutter’s high point. Hold the Gutter Pumper tightly and tighten the nut with its flange side facing towards the Gutter Pumper and tighten. Be careful not to damage the Gutter Pumper’s small vertical pillars. | |

Twist a 20mm class 12 PVC pressure pipe (the internal diameter is 23.7 mm) into the Gutter Pumper, plumb vertically to the bottom of the fascia and fit a 90 degree PVC elbow to plumb a second 20 mm PVC pipe horizontally to the wall. | |

| |

Use pressure pipe clips to attach the pipe to the wall. If a second vertical drop is not used and the pipe is plumbed along the top of the wall to a downpipe or tank, maximising the length of the first drop and increasing the horizontal pipe size to 25 mm will reduce friction loss. | |

Gutter Pumper is usually drained into a downpipe, this is commonly done by fitting a 45 degree PVC elbow to the pressure pipe and then fitting a short PVC pipe to the elbow. The pipe is then fitted into a hole drilled in the downpipe. Seal the gap. Unless blocked, downpipes do not contain less than two thirds air. |

Nearly all Gutter Pumpers are installed as per Method A or Method B

*AS/NZS 2032 states that uPVC pressure pipes installed in direct sunlight must be either painted with light coloured water-based paints or otherwise protected.*

** check local plumbing regulations for scope of allowable DIY work*

- further information -

RECOMMENDED PIPE LENGTH TO SECOND VERTICAL DROP